Ok any electricians or low voltage experts- i have an issue that is driving me batshit crazy. drew a chicken scratch diagram to try and explain. 1 switch with 2 wire going to 1st outlet and then connected to a couple more outlets (3 wire) with all switches half hot half switched. adding an overhead light fixture and tried to hook into 2 wire running from switch but does not work in any configuration. i thought it would but...no mas. my guess is that i can only hook to one of those (switch leg or load) from the light fixture with the other having to tie into another spot on the circuit?! Help!!!